How To Troubleshoot a Jandy AquaPure
Low or No Chlorine
- 1). Add chlorine stabilizer as required. Chlorine stabilizer content should be 50 to 75 PPM. For every 50 pounds of salt, 1.25 pounds of stabilizer should be added.
- 2). Increase the system's daily operating time.
- 3). Increase chlorine production by pressing the "chlorine production rate adjustment" button.
- 4). Enable "boost" mode and run for 24 hours.
- 5). Press the "test salinity" button. If salinity is low, more salt may need to be added.
- 6). Clean the cell if it is dirty or clogged.
Screen is Blank
- 1). Check that the unit is connected to a power supply and the pump is switched on.
- 2). Fully insert into the connector the ribbon cable between front and back PC board.
- 3). Properly connect the connector at the white plug between the transformer and back PC board.
No "Cell On" Indicator
- 1). Ensure "chlorine production" setting is not set to "00%." Adjust to desired percentage.
- 2). Clean and/or unblock cell as required.
- 3). Plug in the "flow/temp/salinity" sensor.
"No Flow" Indicator Stays On
- 1). Unclog the strainer baskets if necessary.
- 2). Correctly align all valves.
- 3). Clean or unclog filter if required.
- 4). Plug in the "flow/temp/salinity" sensor.
- 5). Remove the "flow/temp/salinity" sensor. Clean the sensor and reinstall.